Level Control box used for protection of submersible water pumps used in the supply of pressurized water tanks or cisterns.
Level control in tanks or reservoirs
Protection against water shortage, red led access when there is water level below the minimum level probe (close dry contact to start the electropump to reset level)
Protection against short-circuits by a circuit breaker – 16A
Protection against overloads by an overload relay – IP54 IK07
Lack of water in the tank (red LED on the level relay)
Running motor status(green LED on the level relay)
Overload trip staus (red LED on the level relay)
Make the connections, as indicated on the sticker, with the switch on (off).
Set the thermal relay to the rated motor current.
Switch the switch to automatic (aut).
After contacting the P11 and P12 contacts, the contactor will arm when the water level reaches the minimum level probe (red LED F.A. – water shortage), switching off when the contact pair P11 and P12 open, or if the level Of water rise beyond the maximum level probe (extinguishes the red LED – lack of water).
If the control circuit switch is in the manual (manu) position, the pump switches on regardless of the control status of the contact pair P11 and P12 and the level condition.
In case of tripping of the thermal relay (overload), the pump switches off (red LED D.T. on the level relay), regardless of the information provided by any of the other controls.